What is the Fire Alarm System
A Fire Alarm Systems is for life safety of the public. The system gives audible and or visible warning of a fire in the Building.
It is indicating a fire incident that requires emergency actions such as fire-fighting, emergency services and evacuation from a building.
Once the system identifies the fire with the help of various detectors installed across Building.
It gives the alarm to the occupants of a building of fire through sounders and flashers and calls the fire-fighters through automatic communication.
The components of Fire Alarm are designed and installed as per NFPA 72.
Fire Alarm system uses manually operated devices like pull stations or automatically activated devices like smoke and heat detectors.
Basic Design of Fire Alarm System
Important Components of Fire Alarm System
Smoke/heat detector, Duct detector, Beam detector, Manual pull station, Interface unit, Strobe, Sounder and Sounder/strobe
Fire Alarm System Integration
The Fire Alarm System is integrated with all the system in buildings, below listed system were integrated with Fire Alarm
- Fire Pump
- Electrical Pump
- Jockey Pump
- Fuel Tank
- FOAM System
- ELV System
- Public Address
- Access Control
- Lighting Control
- Central Battery
Basic Working Principle of Fire Alarm System
Fire Alarm system mainly complies with NFPA72 code. Now we’ll see the working of the Fire Alarm system in particular Building.
Let’s take an example of a familiar place we all visit, i.e. Mall.
If the fire initiated inside the Mall, the smoke detector senses the smoke and indicates Fire Alarm Control Panel (FACP),
Fire Alarm Control Panel(FACP) programmed as per the individual building requirements with local civil defence codes and standards. Currently, we will see an example of the Mall.
Here when the detector and indication sense smoke has occurred in FACP, the system specialist along with security is given three minutes to investigate whether it is the real fire or just dust that detector has sensed.
If it’s only dust, then system specialist along with security, acknowledges the FACP and silences the alarm Whereas no further fire signal will be initiated in Building.
If it is real fire then after 3 minutes, FACP automatically gives a signal to sounder/flasher and public address in building to give evacuation message and sound an emergency alarm in Building.
So people in Mall can evacuate the BuildingBuilding immediately, which is the first step FACP initiates, below we are going to see the sequence.
FACP sends the signal to Access Control system to unlock all Entrance Access doors and fire exit doors and other room where general public and staff are inside Mall.
FACP sends a signal to the HVAC system to shutdown AHU, FCU, VRV, MSFD to stop the airflow, which prevents the smoke from spreading around the Mall.
FACP sends a signal to the Lighting control system/central battery system to make sure all lights are ON in the Mall for the public to ensure the route is clear to exit.
FACP sends a signal to BMS to monitor all systems functioning properly during the fire if any system fails then system specialist along with security manually take the necessary action to prevent the fire from spreading and public to exit safely.
Hence Fire Alarm System is installed in Building for public safety. Therefore Fire Alarm System is called as one of Life Safety System.
11 thoughts on “Understand the basics of Fire Alarm system”
Thanks a lot
This is really a super post with a lot of information contained in it. This amazing post helps us to understand the basis of fire alarm system how it can be used and its advantages. It can be really great for people like me who are looking for grabbing more knowledge about it. Thanks a lot. Great to find stsolutions.nz/smart-home-automation-auckland/ which has same kind of wonderful tips, if possible then visit.
Pls, Find the attached Drawings of Fire Alarm System of subject project. Kindly send us best competitive discounted quote along with complete technical data on urgent basis by tomorrow COB.
simple and best things has been very well explained in this post ,
Thanks for sharing such nice information about the fire alarm system . Your explanation is easy to understand. Nice work keep it up
dear, i need a prompt help. I have 20 story building with 3 underground basement(for car parking). should i provide heat detector in car parking area of basement. please suggest me and provide me nfpa clause for this.
Thanks for valuable information in your article , my question is in case of fire if FACP directly shutdown AHU or BMS system is responsible of shutdown the unit ?
Good, simple & under standable.
Thank you so much for sharing good information about fire alarms system.